February 1, 2018 Bradford White
Why is it important to understand combustion air requirements?
Without the proper amount of combustion air, gas fired water heaters will not operate properly and can potentially be harmful.
Symptoms of lack of combustion air
Determining combustion air requirements
A confined space is defined as a room having less than 50 ft. per 1000 BTU/Hr.
Reference National Fuel and Gas Code (NFGC), Chapter 9
An unconfined space is defined as an area having 50 ft. or more per 1000 BTU/Hr.
Reference NFGC, Chapter 9
Requirements for installing a water heater in a confined space
Power direct vent/direct vent
A power direct vent/ direct vent water heater is drawing all combustion air from outside.
Provide adequate combustion air
Communicate directly with an adjacent enclosure or directly outdoors. If direct communication is not available, the use of ducting may be necessary.
Reference NFGC chapter 9 for formulas and requirements.